The reason of choosing insulation piecring connector (IPC)
3.1 Simple installation
Con be branch of cable without striping the insulated coat and the joint is completely insulated.Make branch in the random location of cable without cutting off the main cable.Smiple and reliable installation,just need sleever spanner,can be installed with on live line.
3.2 Safe use
The joint has good resistance to distorion,quake,fire,wet,electrochemical corrosion and aging,need no maintenance,Has been used successfully for 30 years,
3.3 Economical cost
Small installation space.save the cost of bridge and land construction.In structural application.there need no terminal box.junction box and return wire of cable,save cost.The cost of cables and clamps is lower than other power supply system.
General of insulation piercing connector(IPC)
1.1 Piercing connector,simple installation.need
not strip the cable coat.
1.2 Moment nut,piercing pressure is constant,keep good electric connection and make no damage to lead.
1.3 Self-seam frame,wetproof,and anti-corrosion,extend the using life of insulated lead and connector
1.4 A dopted special connecting tablet,apply to joint of Cu(AL)and Cu(AL)or Cu and Al
1.5 Small electric connecting resistance,connecting resistance less than 1.1 times of the resistance of branch conductor with teh same length.
1.6 Special insulated case body,resistandce to illumination and environmental aging.the insulation strength can up to 12kV
1.7 Arc surface design,apply to connectrion with the same(different)diameter,wide connectrion scope(0.75mm2-400mm2)
2.1 Mechanical performance:the grip force of the wire clamp is 1/10 bigger the the break force of the lead.It comply with GB/T2317.3-2000,the heat circle trial standard for elcetic fitting.
2.2 Temperature rise performance:under the
condition of big current.the temperature rise of connector is less than that of
2.3 Heat circle performance:conforms to GB/T2317.3-2000,the heat circle trial standard for elcetirc fitting.
2.4 Waterproof insulation performance:conforms to the relecant requirements in Part 2 of GB/T13140.4-1998
2.5 Resistance to corrosion performance:under the condition of SO2 and salt fog.it can do three times of foureteen days circle testing.
2.6 Environmental aging performance:under the circumstance of ultraviolet.radiation,dry and moist,expose if with change of temperature and heat impulse for six weeks.
2.7 Fire-proof performance:insulation material of the connectror with stands glowing filament test,Conform to the requirements in Chapter4-10 of GB/T5169.4.
Welcome to our website! Please send your words at any time in the following form and ask us, we will contact you and provide you with the corresponding service as soon as possible. Please write in English.